From 1999 to 2010, there were 97 entrapment incidents reported in
the United States — 12 of them fatal. Currently, suction
outlet covers are the only piece of equipment with the ability to
prevent all five types of entrapment. Because of this, the
drain-cover standard, ANSI/APSP-16, outlines
separate tests to address the tragedy in all its forms. Here is a
short definition of each type of test, as well as an explanation of
the entrapment it is designed to stop.
Test procedure: Technicians
install the cover on a flat surface and verify that the pump can
create a vacuum of 26 inches of mercury at the manufacturer-stated
flow rate. A body-blocking element is pressed onto the drain while
technicians measure the force required. For the product to pass,
the amount of removal force must fall under the maximum, dictated
by the cover’s size.
Test procedure: Two key tests are
performed, one using a ponytail and the other a full wig.
Technicians determine which area of the drain allows the most flow,
wave the hair above that zone, and then rest it on the cover for a
set period of time. If more than 5 lbs. of force is required to
remove the hair, the unit will not pass the standard at that flow
rate, and additional tests are conducted.
Test procedure: In addition to
the protocol listed under evisceration, a test is performed to make
sure fingers and other objects cannot penetrate the openings. A
probe designed to simulate a human digit is placed in an opening.
This “finger” is the length of an adult basketball
player’s but the width of a toddler’s. If it penetrates
past a certain point, the cover fails.
Test procedure: Several protocol
help ensure that the cover will remain in place and intact until
its expiration date. Strength and ultraviolet tests ascertain that
the unit won’t deteriorate past an acceptable level. A pull
load test, required on drain covers with holes larger than 0.375
inches, ensures that a person can’t reach his or her fingers
into the openings and lift off the unit.
Test procedure: The combination
of proper flow and tests listed in the hair and limb entrapment
sections help reduce this hazard.